Wondering what temperature your A/C should be blowing into your home?
Well, there’s not a universal, fixed temperature your A/C should always be blowing. The temperature your A/C puts out is relative to the temperature you set on your thermostat.
So even though there’s no single ideal temperature, you do want a 16°–22° F difference from the supply air and return air. Professionals call this temperature difference the evaporator Delta T.
When evaporator Delta T is between 16°–22° F, that means your system is working properly. But if temperatures fall outside of that range, it means your A/C has some issues.
In this article, we’ll go into how you can calculate evaporator Delta T and what issues you could have when air temperatures fall outside the ideal range.
Let’s start by going into more detail about evaporator Delta T...
Just so we’re on the same page, let’s discuss what we mean by supply and return air.
A supply vent register.
Simply put, supply air is the air entering your home through the registers/vents pictured above.
A return air grill.
The air then goes back into your ductwork via the return vent, is cooled, and reenters your home through the supply registers.
Air enters your home through the supply vent, then goes back into the system through the return grill.
The indoor A/C part that actually cools your home’s warm air is called the evaporator coil (pictured as a snowflake in the image above).
When we calculate evaporator Delta T, we’re trying to see how efficiently the coil is working.
So now that you know supply vs. return air, you can calculate evaporator Delta T:
The short answer is, it means something’s not working correctly in your A/C. Let’s look at some common problems:
High evaporator Delta T means that the incoming temperature and outgoing temperature is excessively large. It’s usually caused by low air flow across the coil, which includes problems like:
Learn more about why your A/C is blowing hot air.
Low evaporator Delta T means that there’s an excessively small difference between the incoming and outgoing temperature. Low evaporator Delta T problems include:
Hire a professional to check your system for refrigerant leaks and inspect your valves and ductwork.
Contact George Brazil to schedule an air conditioning repair. We will send one of our trusted professionals to your home to get your A/C back in tip-top shape.
We’ve been keeping Arizona families cool since 1955.